NFPA 99 Chapter 5 Changes
{"Image DocumentName": "NFPA 99 Chapter 5 Changes", "Image ImageDescription": "Control equipment. (New) Controls for central supply systems shall be permitted to be installed remotely as long as it is in a secure location, the enclosure provides enough space to perform maintenance and repair and for all sources except medical air does not communicate with combustible or flammable materials. I.E. \u2013 this allows the supply line from the bulk oxygen to be operated at a higher pressure (125 psig) and branched to the hyperbaric area where it is then regulated to operating pressure (80 psig) and then goes on to the facility where it again is regulated (55 psig) Jim Lucas - Tri-Tech Medical.", "Image XResolution": "37", "Image YResolution": "37", "Image ResolutionUnit": "Pixels/Centimeter", "Image Software": "SlidePlayer", "Image YCbCrPositioning": "Centered"}