WINDOW AIR CONDITIONERS
{"Image DocumentName": "WINDOW AIR CONDITIONERS", "Image ImageDescription": "Compressor, condenser, fan, evaporator, capillary tube in a single unit. Fixed on any external wall or a window (blocks light partially) 5 deg slope to exterior is needed for easy flow of condensate water. Fixing location should serve best possible air circulation. Hermetically sealed (air tight steel shell with compressor and motor) reciprocating, scroll or rotary type compressor is used. Precaution to be taken for hot air released by condenser. Noisy and no uniform air circulation but economical. Lower level fixing helps in easy maintenance and operation. For narrow / long room - high level installation - better air circulation. Adjustable grills are provided to direct air movement. Available from 0.5 to 2 TR suitable for 5 to 20 Sqm. Larger spaces to be handled by multiple units. \u2018Filter clean reminder\u2019 notice & sleep mode facility.", "Image XResolution": "37", "Image YResolution": "37", "Image ResolutionUnit": "Pixels/Centimeter", "Image Software": "SlidePlayer", "Image YCbCrPositioning": "Centered"}