DIGITAL INPUT/FUNCTION: OCCUPANCY (NOT FOR IDROWALL FREND* )
{"Image DocumentName": "DIGITAL INPUT/FUNCTION: OCCUPANCY (NOT FOR IDROWALL FREND  )", "Image ImageDescription": "ONLY x KICM. In case of supervising system (BMS) with OCCUPANCY function it is possible to activate 3 different working modes (by modifying board parameters P45=8; P93=3 trough installer password (60) on the panel): Not booked room = OFF. Occupied room = Comfort mode. Booked and not occupied room = Stand-by/Economy mode. Not occupied OFF. Occupied Comfort mode. There is a person in the room. The fancoil works with desired temperature value for fixed time (15 min). Set-point = desired temperature value. The occupancy status can be activated: By one of the keys in the panel (not ON/OFF) for a set period of time (parameter P94=15 min). At the end of the time periods (15 min) the occupancy status can be enabled again. With movement sensor on DI5 digital input. Pressing Sleep key for 5 sec the Occupancy function continues up to unit switch-off. Booked and not occupied Stand-by/Economy mode. There is no person in the room. The fancoil works with economy set-point for energy savings. Set-point = economy.   Only with ECO (DI4, parameter P44=8) NOTA BENE Con funzione Occupancy abilitata non utilizzare l\u2019ingresso igitale ECONOMY.", "Image XResolution": "37", "Image YResolution": "37", "Image ResolutionUnit": "Pixels/Centimeter", "Image Software": "SlidePlayer", "Image YCbCrPositioning": "Centered"}