Chapter 13 Fuel Supply Part II
{"Image DocumentName": "Chapter 13 Fuel Supply Part II", "Image ImageDescription": "Manufactured Homesite Gas Shutoff Valve. Each manufactured homesite shall have a listed gas shutoff valve installed upstream of the manufactured homesite gas outlet. The gas shutoff valve shall be located on the outlet riser at a height of not less than six (6) inches (150 mm) above finished grade. A gas shutoff valve shall not be located under any manufactured home. The outlet shall be equipped with a cap or plug to prevent discharge of gas whenever the manufactured homesite outlet is not connected to a manufactured home. Exception: All gas shutoff valves for manufactured homes located on foundations constructed in accordance with the local building code or, in the absence of a local code, with a recognized model building code. [NFPA 501A:4.2.2] LANES POINTS.", "Image XResolution": "37", "Image YResolution": "37", "Image ResolutionUnit": "Pixels/Centimeter", "Image Software": "SlidePlayer", "Image YCbCrPositioning": "Centered"}