Appendix G – Table G3.1.1B Baseline HVAC System Descriptions –1: Hot-water boiler(s) and PTACs (6.8.1D&F) 80% AFUE-82% Et and 9.3-11.0 EER Pumps: 19 W/gpm, Supply @180F, Return @130F Outdoor reset (G3.1.3.4) –2: Packaged terminal heat pumps (6.8.1D) 9.1-10.8 EER and 2.8-3.0 COP 6.8.1D Example:12.3-(0.213*Capacity/1000) EER Auxiliary heat only when outdoor temp is < 40F –Supply Fan Power: CFM X 0.3 (G3.1.2.9)
{}