5.3. Cleanrooms and isolators in the controlled area (2/3)
{"Image DocumentName": "5.3. Cleanrooms and isolators in the controlled area (2/3)", "Image ImageDescription": "The cleanroom for production of FDG (33) should house the hot cells for the synthesis modules, (35), (typically two modules are used for redundancy in separate hot cells), the hot cell for the dispenser (36), a laminar flow hood, (37), and a workbench. The FDG production cleanroom should be located as close as possible to the cyclotron and the hot cells should be installed along the wall that is closest to the cyclotron in order to reduce the losses of 18F in the capillary used for the transfer of irradiated enriched water. The hot cells should be located in the cleanroom so that the doors can be fully opened in order to access the modules for preparation or service. The inner containment enclosure and the air quality inside the hot cells housing the production modules should be GMP class C.", "Image XResolution": "37", "Image YResolution": "37", "Image ResolutionUnit": "Pixels/Centimeter", "Image Software": "SlidePlayer", "Image YCbCrPositioning": "Centered"}