IEBC Fire Protection Requirements
{"Image DocumentName": "IEBC Fire Protection Requirements", "Image ImageDescription": "Section References: Repairs & Alterations Level 1, etc. (503.1, 603.1, ) shall be done in a manner that maintains the level of fire protection provided. Major Alterations (503.2, 603.2, , 804.1): Automatic sprinkler systems may be required in building undergoing major alterations per section Scope (704.1): The requirements of this section shall be limited to work areas in which Level 2 alterations are being performed, and where specified they shall apply throughout the floor on which the work areas are located or otherwise beyond the work area. Corridor ratings ( ): Where an approved automatic sprinkler system is installed throughout the story, the required fire-resistance rating for any corridor located on the story shall be permitted to be reduced in accordance with the IBC. In order to be considered for a corridor rating reduction, such system shall provide coverage for the stairwell landings serving the floor and the intermediate landings immediately below. Automatic sprinkler systems (704.2): Automatic sprinkler systems shall be provided in accordance with the requirements of Sections through Installation requirements shall be in accordance with the IBC High Rises, A, B, E, F, etc. and mixed uses, (MA amendment exception pertains to R-2 of three units) Windowless stories, Other suppression systems, Supervision.", "Image XResolution": "37", "Image YResolution": "37", "Image ResolutionUnit": "Pixels/Centimeter", "Image Software": "SlidePlayer", "Image YCbCrPositioning": "Centered"}